;Sample XMULTI_Installation_Assistant language file_English
;Usage:
;1.Translate everything at the right side of '='.
;2.Run XMULTI_Installation_Assistant and select your language to see the result.
;3.Any un-translated words will be shown in english.

[GENERAL]
;---------------------------------------------------------------------------------
name=XMULTI_Installation_Assistant  ;Don't modify this line for file verify check.
author=hero.feng                    ;Don't modify this line for file verify check.
;---------------------------------------------------------------------------------
language=English(&E)
languageSelection=Language &select...

[MENU_SYSTEST]
M0=System&Test
M0M0=Comm Port
M0M1=&Start
M0M2=&Pause
M0M3=&ReTest
M0M4=&Quit

[FORM_MAIN]
Name=X-MULTI Installation Assistant [all types compatible]

[TAB_INSTALLATION]
Caption=  Installation Info.
Label_0=UnitA
Label_1=UnitB
Label_2=UnitC
Label_3=UnitD
Label_4=UnitE
Labe2_0=No Indoor
Labe2_1=No Indoor
Labe2_2=No Indoor
Labe2_3=No Indoor
Labe2_4=No Indoor
Labe3_0=Drag and drop indoor units to the position Unit ABCD. Double click to remove the indoor unit.
Labe3_1=Wall mounted (V)
Labe3_2=Wall mounted (H)
Labe3_3=Cassette
Labe3_4=Slim Duct
Labe3_5=Floor Ceiling
Labe3_6=Console

Labe4=Please select the outdoor unit and indoor units type for a system match report.
Labe5=Refrigeration System Clock
Labe6=Indoor capacity is much higher than outdoor capacity. Match ratio should be better within 135%.

Text1=No Indoor Unit
Text2=Outdoor Unit
Text3=Indoor Unit
Text4=Match Ratio
Text4=Recommended Ratio
CommandButton=Selection  &OK
Text5=Installation information report...

[TAB_OPERATION]
Caption=  Operation Info.
Label= Click here for abbr Description
Labe2=Outdoor Unit System Data
Labe2_0=Run State
Labe2_1=ForcedRun
Labe2_2=RatedRun
Labe2_3=Diagnostic Code:                            0 - Normal
Labe2_4=Target Freq
Labe2_5=Run Freq
Labe2_6=Fan State
Labe2_7=4WV
Labe2_8=SV2
Labe2_9=PTC
Labe2_10=Heater
Labe3=Outdoor Unit Sensor Data

Labe4=Indoor Units Data
Labe4_0=IndoorID
Labe4_1=Unit A
Labe4_2=Unit B
Labe4_3=Unit C
Labe4_4=Unit D
Labe4_5=Unit E
Labe4_6=HP        
Labe4_7=RunMode
Labe4_8=Tset     
Labe4_9=Tai      
Labe4_10=Tc1      
Labe4_11=Tc2     
Labe4_12=Tm       
Labe4_13=PMVtar 
Labe4_15=PMVrun
Labe4_15=FanSpeed
Labe4_16=Pcode   
Labe4_17=DiagCode    
Labe5_0=Unit A Diagnostic Code:                0 - Normal
Labe5_1=Unit B Diagnostic Code:                0 - Normal
Labe5_2=Unit C Diagnostic Code:                0 - Normal
Labe5_3=Unit D Diagnostic Code:                0 - Normal
Labe5_4=Unit E Diagnostic Code:                0 - Normal
Labe6_0=ON-
Labe6_1=OFF-
Labe7=Defrost Accumulative Time

[TAB_TestReport]
Caption=  Test Running Report
Label=After 20 minutes,system test information could be reported.
Labe2=If everything is OK,then show "OK";otherwise show "NO" and the solution be showed at the same time.
Label3_0=Unit
Label3_1=Outdoor
Label3_2=Indoor A
Label3_3=Indoor B
Label3_4=Indoor C
Label3_5=Indoor D
Label3_6=Indoor E
Label3_7=TestTimes
Label3_8= 1 Times    
Label3_9= 2 Times    
Label3_10= 3 Times    
Label3_11= 4 Times    
Label3_12= 5 Times    
Label3_13=     Average   
Label3_14=     Conclusion

[TAB_AbbrDescription]
Caption=  Abbr Description
Label=Outdoor Unit Abbreviation Description
Labe1_0=Target Freq - Target frequency
Labe1_1=Run Freq - Running frequency
Labe1_2=Fan State -  The class of out fan speed
Labe1_3=4WV - 4 way valve
Labe1_4=SV2 - Spurt valve
Labe1_5=Heater - Crankcase heater
Labe1_6=Tmave - Working indoors' Tm average value
Labe1_7=Tc2ave - Working indoors' Tc2 average value
Labe1_8=Td - Discharge temperature
Labe1_9=Ts - Suction temperature
Labe1_10=Te - Defrost temperature
Labe1_11=Tao - Outdoor ambient temperature
Labe1_12=Tc - Condenser middle temperature
Labe1_13=Toci - Gas pipe temperature of condenser
Labe1_14=Fin - IPM fin temperature
Labe1_15=Idc - DC current
Labe1_16=Imtr - Motor current
Labe1_17=Tc2max - the maximum of the working                        indoors' Tc2 temperature
Labe2=Indoor Units Abbreviation Description
Labe2_0=HP - Horese power
Labe2_1=RunMode - The indoor unit run mode
Labe2_2=Tset - The set temperature
Labe2_3=Tai - Indoor ambient temperature
Labe2_4=Tc1 - Gas pipe temperature
Labe2_5=Tc2 - Liquid pipe temperature
Labe2_6=Tm - The evaporator middle temperature
Labe2_7=PMVtar - Target PMV step
Labe2_8=PMVrun - PMV step
Labe2_9=FanSpeed - Indoor unit fan speed

[TAB_TroubleShooting]
Caption=  Trouble Shooting
Label=to be continued...

[PGM_TEXT]
Text1=None
Text1=Flash 1 time,01:Indoor ambient temp
Text1=Flash 2 times,02:Indoor gas pipe sensor TC1 faulty
Text1=Flash 3 times,03:Indoor liquid pipe sensor TC2 faulty
Text1=Flash 4 times,04:Indoor exchange middle temp.sensor Tm faulty
Text1=Flash 5 times,05:Indoor EEPROM faulty
Text1=Flash 6 times,06:Com faulty between indoor and outdoor units
Text1=Flash 7 times,07:Com faulty between indoor and wired controller
Text1=Flash 8 times,08:Indoor water pump abnormal
Text1=Flash 9 times,09:Indoor address repeat for communication
Text1=Flash 10 times,10:Indoor address repeat for central controller
Text1=Flash 11 times,11:Indoor PG fan motor abnormal
Text1=Flash 12 times,12:Power abnormal
Text1=Flash 20 times, & i & :Outdoor faulty

Text1=Diagnostic Code:Normal
Text1=Flash 1 time,20:Defrost temp. sensor TE abnormal
Text1=Flash 2 times,21:Ambient temp. sensor TA abnormal
Text1=Flash 3 times,22:Suction temp. sensor TS abnormal
Text1=Flash 4 times,23:Discharge temp. sensor TD abnormal
Text1=Flash 5 timers,25:AC current abnormal
Text1=Flash 6 times,26:Com faulty between indoor and outdoor units
Text1=Flash 9 times,30:High pressure switch problem
Text1=Flash 10 timers,31:Low pressure switch problem
Text1=Flash 11 times,32:IPM protection problem
Text1=Flash 12 times,33:EEPROM problem
Text1=Flash 13 times,34:Discharge temp. over-high
Text1=Flash 14 times,35:Compressor discharge temp. over-heat
Text1=Flash 15 times,36:DC fan motor abnormal
Text1=Flash 16 times,37:4 way valve state abnormal
Text1=Flash 17 times,38:Outdoor exchange middle temp. sensor TC abnormal
Text1=Flash 21 times,42:Outdoor gas pipe sensor TOCI abnormal
Text1=Flash 23 times,57:The voltage of IPM is too low
Text1=Flash 24 times,58:The voltage of IPM is too high
Text1=Flash 25 times,46:Com faulty between PCB and IPM module
Text1=Flash 26 times,50:Compressor is blocked
Text1=Flash 27 times,51:Compressor vibration problem  
Text1=Flash 28 times,52:Compressor running in wrong state
Text1=Flash 29 times,53:The start steps of compressor abnormal
Text1=Flash 30 times,55:Testor abnormal
Text1=Flash 31 times,56:Compressor is damaged